- remote access to device using MODBUS RTU protocol
- datalogger for measured data
- Aluminium case – high electromagnetic interference resistance
- Vybrat příslušenství
- Product description
- Technical specification
- Commercial packaging
GSM-MODBUS-485 is intended for remote access to devices with RS485 using protocol MODBUS RTU. Via this protocol is possible to read or write data from customers technology. These data can be process, transform to user´s units or send warning SMS according the set conditions. Datalogger is included in GSM-MODBUS-485 and keep measured data and actions. Datalogger is either in internal memory or you can use Google Spreadsheet for data storage. Usual devices are smart sensors, frequency converter, electricity meter, water meter or even PLC. GSM-MODBUS-485 supports MASTER mode.
Remote control means to get a SMS whenever a register in monitored device goes out of limits or a way to change values in registers of connected device.
Beside the serial port GSM-MODBUS-485 is equipped with one auxiliary digital input and one digital output. The inputs can watch digital output of connected device and the output can be used to reset monitored device in case of emergency. Predefined registers in connected devices can be queried via SMS.
GSM-MODBUS-485 is possible to mount on the DIN rail using DIN rail holder GSM-75-DIN, which is supplied separatelly.
We offer free program SeaConfigurator for detailed configuration. The GSM-MODBUS can be configured either via USB port or remotely via GPRS connection to the internet.
- SW for this unit include MODBUS Master RTU
- For connection to PLC FATEK is sufficient to set names of inputs / outputs (X0,X1…Y0, Y1…).
- The configuration is made by programm SeaConfigurator via USB connector or remotely via GPRS.
- Extension for PLC – remote control and sending states (alarms) via SMS
- Clever electrometer – sending consumption from electrometers with RS485 and protocol MODBUS
- PLC controlling the pump – guarding overflow, error status, remotely switch on/off
- Diesel generator set – guarding low or critical oil level, determine working hours and other data
- Remote control of any appliance with protocol MODBUS
- Basic communication via SMS messages
- Connection to the appliance: serial port RS485, protocol MODBUS RTU
- Remote control of appliance´s outputs : typically on PLC FATEK
- Remote state detection of digital and analog inputs: typically on PLC FATEK
- Possibility to connect several devices at the same time
- Configuration: from PC program SeaConfigurator via USB connector
- Built-in accumulator: Li-Ion (enable to report power supply failure via SMS message)
How MODBUS-485 works:
- Firstly you must configurate the type of communication MASTER and port speed.
- For selected registers you fill modbus address and define sending SMS when the register is changed. For PLC FATEK is possible to define address as the name of register in FATEK format.
- For control is possible to define names for commands, by which you can set the register values in connected appliances. Some configuration (parameters setting) can be done via SMS – see the chapter “List of commands” in a User manual.
- Then GSM-MODBUS-485 guards values in pre-defined registers during the operation.
- If the register is type Input Discrete (X) or Coil (Y), it is possible to configurate sending SMS when the register is changing L->H or H->L. You can set delay and the name of register.
- If the register is Input Register (A) or Holding Register (B), the read value is compared with configured zones and if there is the zone change, it is possible to send SMS. The typical example is the “temperature guard”. If the temperature falls under the MIN zone or exceeds MAX zone, SMS message is send. You can set delay, the name of transition between 3 zones, number of decimal places and units.
- Anytime it is possible to find out the complete state of registers.
There is a self-adhesive antenne in the commercial package, which is determined for sticking on a plastic box. If you have a metal box, it is better to use an antenna with a magnetic holder. If you state it in your order, we will send you a magnetic antenna GSM-ANT01S instead of self-adhesive one fro free.
For extension you can use PLC FATEK. An example of use is zde.
|Supply Voltage||8 Vdc up to 30 V dc ( typical 12 Vdc )|
|Maximum consumption||3.3 W ( discharged battery, active GSM call, closed output )|
|Standby consumption||12V/90mA ( signed into GSM )|
|Logic output||1 ( relay 2A/60V on separate terminals )|
|Logic inputs||1 ( optocoupler max 30Vdc )|
|Communication port||RS485 (not galvanically isolated)|
|Other parameters||see manual ( in section “Support” )|
MODBUS data types:
- INT32 (MSB)
- UINT32 (MSB)
- INT32 (LSB)
- UINT32 (LSB)
- FLOAT (MSB)
- FLOAT (LSB)
Float is by IEEE, Standard 754.
User Manual …WE PREPARE…
SeaConfigurator (software for setting up and monitoring of GSM devices SEA s.r.o.) GSM-CONFIGURATOR